To avoid the ongoing risk of legionella our client required an old cooling tower to be removed and replaced with an efficient and economical system. Integral replaced the cooling tower with an indirect cooling system. This allowed some existing components to be reused.
The cooling tower was removed from the system, the pipework reconfigured and diverted into a Plate Heat Exchanger.The other side of the heat exchanger saw the introduction of a duplex pumping station c/w with 3 way capacity control valve. The addition of a Daikin Air Cooled Chiller provided approximately 500kW of heat rejection to the process water.
The old basic panel was replaced with a new bespoke control system that automatically controlled not only the process side, but also the Chilled Water system. Following some initial preparation the work was carried out over a long bank holiday weekend shutdown. Production was handed back to the client following successful hot trials at 2pm as per the tight deadline.
Hello! Welcome to our new web site. This site is not fully supported in Internet Explorer 11 (and earlier) versions. Please upgrade your Internet Explorer browser to a newer version.
As an alternative, you can use either of the options below to browse the site: